Q. "I noticed that the interceptors with a 6" NPT inlet and outlet can be furnished with an 8" NPT inlet and outlet. Does that change the dimensions of the interceptor?"
A. Yes. The 'C' dimensions will change to 42". The 'D' dimensions will change to 35" and the 'E' dimensions will change to 5 3/4".
Q. "What are the maintenance requirements for the Z1185 lint interceptors?"
A. Cleaning should be done on a regular basis. Remove the cover and clean out any large debris from the first chamber and accumulation of lint in the second chamber. Remove secondary screen assembly and clean off any lint build up. Reinstall the secondary screen into the interceptor. Make certain the cover gasket is intact and clean. Apply a light coating of oil on the cover gasket, which helps prevent the cover gasket from adhering to the cover and aids in maintaining a complete seal. The cover should then be placed back on the unit and secured. Efficiency of operation is directly related to the level of maintenance.
Q. "How come models Z1185-3 and Z1185-7 are not furnished with lift handles?"
A. The Z1185-3 and Z1185-7 don't come with lift handles because they are small units, and the lids are light enough to lift off the bases without the use of handles. To do this, simply unscrew the four screws located on the lid (one screw is located at each corner). Then you will need to unscrew the middle screw and you will be able to lift the lid off of the base.
We hope that we have helped you on this page with commercial lint traps,
and thank you for helping to make PlumbingSupply.com® the most famous Internet plumbing supplier.
Is there something else that you are looking for?