|Our motto: "under-promise...over-perform"|
Simple, straightforward and low shipping rates for these expansion tanks.
Q. "What is thermal expansion?"
A. When water is heated, it expands in volume by 2 - 3%, depending upon the initial and final temperature. This can mean as much as three or four extra gallons of water in a closed system. If there is no demand for hot water, the expanded volume of water has no place to go. Since water is not compressible, the expanded water cannot be accommodated in the piping system, and therefore it creates hydraulic pressure, exerting a potentially hazardous stress on the system.
Q. "What is a closed system?"
A. It is a system that uses a pressure reducing valve when water service pressure is too high for residential applications, usually above 80PSI.
Q. "What size expansion tank should I order for my water heater?"
A. This depends on the size of your water heater and your water pressure. For most small water heaters usually the A101 works. Please refer to this thermal expansion tank quick-sizing chart to find the appropriate thermal expansion tank for your system.
We hope that we have helped you on this page with thermal expansion tanks,
and thank you for helping to make PlumbingSupply.com® the most famous Internet plumbing supplier.
Is there something else that you are looking for?